Remote light indicator MHS 408 is an element of Fire Detection and Fire Alarm System, which is used as parallel signalling of fire from one or more detectors connected to a line (loop).
It is intended for connecting to all types of addressable and conventional (non-addressable) smoke detectors LITES.
Remote light indicator is intended primarily for use in places where due to higher mechanical requirements other types of signalling cannot be used. Further for signalling states of detectors placed in explosive area, while the remote light indicator MHS 408 must be placed outside of this area.
For connection to an appropriate smoke detector the signalling light is mounted to MHY 713 or MHY 703 base..
|Power supply||6 – 8 Vimp (addressable and conventional voltage detectors)|
|6 – 24 Vimp (conventional current detectors)|
|Current consumption||max. 30 mA|
|Cross-section of connectable wires||0,2 ÷ 2,5 mm²|
|Protection according to ČSN EN 60592||IP 54 (with base MHY 703 or MHY 713)|
|Radio screening degree||B-class equipment according to ČSN EN 55022|
|Dimensions||ø127 × 92 mm|
|Weight||cca 0,5 kg|
Product is intended for operation with safe equipment in sense of ČSN EN 60950.
|The MHS 408 is intended for the interior of objects without occurrence of aggressive substances, and for places where its protection and climatic immunity conform, and where sudden temperature changes leading to dew and ice accretion don`t occur.|
|Working temperature range||-25 °C to +70 °C|
|Relative humidity||max. 95% at +40 °C|
|Atmospheric pressure||60 to 106 kPa|
|Operational position||arbitrary (according to design)|