The Manual call point MHA 145 is intended for manual fire signalling by a person discovering the fire. It is used for the analogue addressable system or conventional loops of Fire Detection and Fire Alarm System LITES.
The Manual call point MHA 145 is intended for use at places unprotected against weather influences wherever it suits its IP protection and climatic resistance. The Manual call point MHA
145 meets requirements of standard EN 54 -11.
The Manual call point connects to the addressable C.I.E. MHU 109, MHU 110, MHU 111, MHU 115, MHU 116, MHU 117 and conventional C.I.E. MHU, 102, MHU 103, MHU 106, MHU 108 and MHU 113.
The Manual call point can be used in addressable system or in conventional system with current and voltage detection loops as a direct replacement of MHA 101, MHA 144, MHA 181, MHA 182 a MHA 183.To the Manual call point can be connected Remote Indicator MHS 409, MHS 408, eventually MHS 407. Addressing and setting of a Manual call point is carried out using preparation MHY 535.
|Power supply||20 (-3/+1) Vimp addressable C.I.E. LITES|
|Equivalent current||120 μA|
|Range of setting address||1 ÷ 128|
|Power Supply||(16 ÷ 24) Vss|
|Nominal power supply||21,5 VSS|
|Current during fire alarm|
|current regime||20 (-5 až +1) mA|
|voltage regime||max. 100 mA (limited by C.I.E.) (5,7 ÷ 8) V by 10 mA|
|Optical signalling detector||red LED|
|Protection according to ČSN EN 60 529||IP 65|
|Radio screening degree according to ČSN EN 55 022||B-class equipment|
|Cross-section of attachable conductors||(0,1 ÷ 1,5) mm2|
|Size of vista||(70 x 70) mm|
|Mechanical protection of button||glass plate|
|Dimensions w x h x d||130,5 x 133 x 77|
|Weight||cca 1,1 kg|
|The Manual call point is intended for stationary use in areas unprotected against weatherproof with classification according to ČSN EN 60 721-3-4:|
|Working temperature range||-20 °C to +70 °C|
|Relative humidity||max. 95 % at 40 °C (85% to 95% / ≤ 40 °C) 100 hours./year|